1. Telecom riser ducts are reserved for exclusive use by Public Telecommunication Licensees (PTLs) and Telecommunication Service Licensees (TSLs) referred to as FBOs, who provide fixed services to buildings. Any other party who use the riser ducts shall seek permission from IMDA.
2. These guidelines are applicable to In-Building Terrestrial Telecommunication System Licensee (IBTSL) who are required to apply to IMDA to lay cables in telecom riser ducts of commercial buildings or within the telecom conduits of HDB's Electrical and Telecom (E&T) riser ducts. In some HDB estates, telecom conduits run vertically through floors as metal or wood trunking or as uPVC pipes and not located within E & T riser ducts.
Figure 1 and 2 show typical Telecom Conduits in HDB E&T Riser Duct. Figure 2 shows the conduit with the cover removed to expose the cables.
Approval for Use of Riser Duct or Conduit
3. IBTSL are required to write to IMDA to seek approval each time telecom riser ducts or conduits are to be used. These conduits can be constructed of metal (Figure 1) or of other material like wood or plastic.
4. Before applying to IMDA for use of riser ducts or conduits, an IBTSL is required to first explore other possibilities of using other facilities.
5. Approval for use of riser space will be granted on a case-by-case basis and on the availability of space in the riser or within the conduit. Where installing cables in conduits is concerned, the total cross-sectional area of the cables and ancillary devices and joints shall not exceed 10% of the cross-sectional area of the conduit (see figure 4).
Figure 4 - Cross-section (plan view) of a typical E&T riser duct in modern HDB Estates.
6. Upon obtaining IMDA's approval, an IBTSL is advised to consult building owners or in the case of HDB estates, HDB and/or Town Councils to gain access to and carry out installation in riser ducts.
Submission of Information
7. When applying for approval to use a riser duct or a conduit, an IBTSL is required to provide the following information:
7.1. Details of the proposed installation work, including the quantity and sizes of cables; proposed cable position in the rise; the network configuration drawing indicating the segments of cables which will be installed within the riser ducts or conduits;
7.2. Pictures (preferably soft copies) of the riser ducts indicating the dimensions of the risers, sizes of cable trays/conduits and the proposed cable locations. Pictures submitted should indicate the lowest, highest and a floor in between (most congested) where the cable is intended to run through;
7.3. Where pictures mentioned in paragraph 7.2 are not available, the applicant must provide existing layout plans of the riser/s with measurements indicating the proposed cable location; and
7.4. Where installations are carried out in multiple telecom riser ducts or conduits, the IBTSL is required to submit a typical floor plan showing in totality the number of installations and to indicate each installation with "X"s.
Installation of Cables in Riser Ducts or Conduits
8. An IBTSL who has been approved to install cables in a riser duct or a conduit is required to:
8.1. Provide a separate cable tray or metal/plastic (PVC) trunking to house cables in the riser ducts of commercial buildings. Where cables are to be installed within conduits in HDB estates, the cables shall be installed with no encasement.
8.2. Clearly mark all of their installation and own cables installed for easy identification of owners. The labels or markings shall be made of durable material and shall be fasten properly or imprinted/embossed on the cables;
8.3. Ensure that no active devices are installed in the riser ducts;
8.4. Ensure that all cables are properly tied to the cable tray and neatly laid. All such cables shall be laid in such a way that it will not obstruct work space of other users or become a safety hazard;
8.5. Ensure that all floor opening holes are sealed according to the IMDA's COPIF technical requirements when punching through floors during the laying of cables; and
8.6. Ensure proper housekeeping after completion of the works.
8.7. Provide upon completion of works, pictures of the installation in the riser or conduit (as the case may be). The submission of these pictures shall be in A4 paper and shall:
8.7.1. Indicate the building name and the floor the picture was taken;
8.7.2. Capture the dates the photographs were taken;
8.7.3. Indicate/identify the Licensee's cables and supporting structures for the cables and highlight the distinguishing markings; and
8.7.4. Indicate the point of entry and exit in the floor opening.
9. Where necessary, IMDA may require a joint site survey with an IBTSL to ensure that all requirements of IMDA are complied with.
IDA's Right to Refuse Access to Risers or Conduits
10. When a riser duct or conduit has been fully utilised and it is not feasible to accommodate lying of additional cables, IMDA may refuse access to or installation of any cables in the riser or conduit, notwithstanding the IBTSL has satisfied the requirement as stated in paragraphs 3,4, 5 or 6.
11. Where the IBTSL has been permitted by IMDA to use the riser duct or conduit and the usage has impeded the laying of cables and other support structures by an FBO, IMDA may require the IBTSL to make the necessary alteration or adjustment to its installation at its own cost to accommodate the requirement of the FBO. In the event that such alternation or adjustment is not feasible, IMDA may require the IBTSL to remove its installation at its own cost to make way for the installation by the FBO.
12. When an FBO's laying of cables or other support structures in the riser duct or conduit is impeded by cables already installed in the riser by the IBTSL without IMDA's approval, IMDA will require the IBTSL to remove the cables. The cost of such removal shall be borne by the IBTSL who shall also undertake to indemnify IMDA of all liabilities that may arise therefrom.
Removal of Cabling Installation
13. An IBTSL who is no longer operating in the building and where cables laid are still in use by other parties, shall not remove any part of the cables or cabling support structures from the riser duct or conduit without IMDA's approval.
14. Where the cables laid by the IBTSL are no longer in use and there are no other parties interested in taking over ownership of the cables, the IBTSL must recover the cables and the support structures at its own cost from the riser duct or conduit and inform IMDA of such removal.
Review of Guidelines 15. These guidelines are subject to review from time to time by IMDA to take account of changes of regulatory environment and policy.
Enquiry or Clarification
Any enquiry or application for the use of risers is to be forwarded to:
Director, Interconnection & Access
Infocomm Media Development Authority of Singapore
10 Pasir Panjang Road #03-01
Mapletree Business City
Fax: +65 6211 2116
IMDA and United States Federal Communications commission signed MOU to promote bilateral cooperation
The Infocomm Media Development Authority (IMDA) of Singapore and the United States Federal Communications Commission (FCC) have...
Nominations for 3rd edition of 100 Women in Tech list now open
Public invited to nominate women who are making an impact on Singapore’s tech industry “Girls in Tech” category returns for female...
Singapore and the European Free Trade Association launch negotiations on Digital Economy Agreement
Singapore and the European Free Trade Association (EFTA) have launched negotiations on an EFTA-Singapore Digital Economy Agreement...
Singapore and the European Union Sign Digital Partnership
Minister-in-charge of Trade Relations S Iswaran and European Commissioner for Internal Market Thierry Breton signed the...
Singapore firms can now tap on Temus-IMDA's talent conversion programme to fill tech roles
Singapore’s Minister for Communications and Information Mrs Josephine Teo officiated the launch of Temus’ Step IT Up programme...
Enhanced measures against scam SMS
As part of the measures announced by the Infocomm Media Development Authority (IMDA) in October last year, all organisations that...
IMDA and ACMA signed Memorandum of Understanding for enhanced cooperation to combat scam and spam communications
Infocomm Media Development Authority (IMDA) and Australian Communications and Media Authority (ACMA) signed Memorandum of...
The Korea-Singapore Digital Partnership Agreement Enters into force
The Korea-Singapore Digital Partnership Agreement (KSDPA) will enter into force on 14 January 2023. The KSDPA was signed by Second...
IMDA announces a $5 million fund to support Singapore’s media industry to adopt virtual production
To ensure that the local media industry remains competitive as the international partner of choice to create premium IP, the...
20 Industry Digital Plans, which have contributed to the uplifting of more than 85,000 businesses, will be progressively refreshed, with the Food Services Sector being the first to benefit from the refreshed model
The refreshed Food Services Industry Digital Plan will include a refreshed Digital Solution Roadmap, introduction of a roadmap...